Ideal for heating industrial halls, warehouses, sports facilities,
workshops and smaller establishments.
Option to instal on the wall and on the ceiling
with a tilt adjustment option of +-30, 60° thanks to
the console included in the package.
In winter, it is used to heat the space to the required temperature.
In summer, it replaces air conditioning with air cooling.
High heat and air output
air flow up to 4700 m3 / hour, heat output 3-71 kW, horizontal air reach up to 17 m, vertical air reach up to 10 m
Quiet operation and high efficiency
Currently the quietest device on the market in its category. Significantly lower consumption.
We use only quality components
Reliable maintenance-free fans, high-quality copper exchangers, powder coating - all this allows to provide a five-year warranty
Possibility to continuously regulate the fan speed
Continuous speed control is enabled by used EC motors. We recommend using the Elementair-E MARK I controller.
When using a filter, the heat exchanger is protected against clogging
|ATACAMA 2||ATACAMA 3||ATACAMA 4|
|Indicative serving area (ceiling height of 4 meters)||m²||0-300||-||0-500||-||0-1000||-|
|Heat output range||kW||3-32||4-39||4-38||5-44||9-58||11-71|
|Heat exchange - rows||-||2||3||2||3||2||3|
|Water exchanger properties||maximum operating water temperature 120 ° C; maximum operating pressure 1.6Mpa; pipe connection dimension G 3/4 "|
|Air reach - horizontal||m||13||12||17||14||15||12|
|Air reach - vertical||m||8||7||10||8||8||6|
|Weight / with console||kg||15 / 17,5||16 / 18,5||17 / 19,5||18 / 20,5||23 / 26||25 / 28|
|The volume of water in the exchanger||dm³||1,4||2,1||1,4||2,1||2||3|
|Power supply||V/Hz||1 ~ 230/50-60||1 ~ 230/50-60||1 ~ 230/50-60|
EC motor power adjustment is necessary feature for setting the required performance of the equipment. This parameter is used as a basis for other parameters of the equipment, which influence the working comfort in the given area - such as air output, temperature and noise level. Electricity consumption, depending on the life cycle of the unit, is no less important of a parameter.
Heating power of the units is the most important parameter for the economical operation of heating of the building. A room thermostat or temperature sensor is required for correct functionality of temperature control. The placement of the
thermostat in the general presence zone outside of the door, window openings and sources of radiant heat at a height of approximately 1.5 m (reference point) is very important.
Air heating is one of the most dynamic heating systems. Air heating is a system where the heat energy is supplied to the heated room exclusively via the flowing hot air from the unit. The principle of functioning of the hot air unit is based on the heat transfer the water exchanger to the surrounding air. Using an axial fan, the air is distributed to the heated space. Air heating is suitable for spaces where a radiant heat source is not desirable.
Mixing or destratification is the principle of mixing the air with the result of an effective temperature distribution throughout the whole volume of space (the warmer air at the ceiling is mixed with colder air at he floor).